Uninterruptible Power supply. Digital Energy™. SitePro. 10 – 15 – 20 – 30 – 40 kVA. Vac CE / Series 8. GE Consumer & Industrial SA. SitePro, the most reliable Uninterruptible Power System available for data security and other demanding critical applications. GE Consumer & Industrial. Power Protection. Digital Energy™. SitePro. ®. Series UPS. Uninterruptible Power Supply 10 – kVA. GE imagination at work.
|Published (Last):||17 December 2005|
|PDF File Size:||16.54 Mb|
|ePub File Size:||7.11 Mb|
|Price:||Free* [*Free Regsitration Required]|
GE DIGITAL ENERGY SITEPRO VAC CESERIES 7 OPERATING MANUAL Pdf Download.
The meaning of the alarms on the free contacts in standard configuration default is the following: The control bus connection between parallel units must be made on the front of the electronic module fitted behind the front door Fig. When the siteoro system detects a fault in the Inverter, siteppro overload condition or a short-circuit condition, the Automatic Bypass will transfer the critical Load to the Mains without interruption.
N p a ra m e te rs Tel1 This parameter specifies a first telephone number to be used for modem dial-out.
sitwpro The outputs of parallel units are connected to a common power bus, and in normal operation the units connected on the parallel bus share the Load equally. Event Report Sitepro 7. Service And Technical Support Fig. Page 3 Please carefully read the Witepro Manual. This first parameter level in not protected by password, therefore the user can freely adapt these parameters to their needs. Epo emergency Power Off 9.
The non-observance of the warnings reminding hazardous situations could result in human injury and equipment damages. In case of any damage sustained during transport, immediately inform the carrier and contact your local Service Centre.
GE UPS sitepro KVA service check alarm | All About Circuits
The screen contents during Edit mode is: Remove the cable short-circuiting terminals X2 when using this external switch. Weekday – Saturday – Sunday – Monday – Tuesday One unit of the system has to be turned Off, while the load sitfpro shared between the other units supplying the parallel bus.
Not only the Inverters but also the Bypass functions are redundant. Close the input switch Q4 — As for the single version.
SitePro UPS 400Vac / CE GE Consumer & Industrial August 2004.
Telephone numbers m e te rin g Tel1: SitePro UPS is a three-phase, on-line, intelligent system for centralized power protection. The information displayed includes: Close the output switch Q1. Page 42 Status load screen This screen displays: A detailed report of the damage is necessary for any insurance claim.
Sizing of circuit breakers, fuses and cables for input mains, output load and battery must meet the requirements of local and national electrical codes. This is the only printer-interface supported by the UPS. Table of Contents Add to my manuals Add. Page 54 Example 2: The UPS cabinet is sitspro standing and normally does not require bolting to the floor.
Digital Energy SitePro® UPS 10-500 kVA
Comments to this Manuals Your Name. Please be sure to have a serial printer, that is a printer with a serial RS interface. Unpacking For parallel systems, the delivery also includes the bus control cables for inter- connecting the UPS modules.
All SitePro UPS models operate in double conversion mode providing true on-line operation and are fully compliant with international standards regarding VFI operation. The UPS must be moved in upright position. The safety screens are fixed in their position.
Output Signals On Voltage-free Contacts 9. While every care has been taken to ensure the completeness and accuracy of this manual, GE assumes no responsibility or liability for any losses or damages resulting from the use of the information contained in this document.
TX out Pin 3: Top Cable Entry Box The present publication and any other documentation supplied with the UPS system is not to be reproduced, either in part or in its entirety, without the prior written consent of GE.
This innovative feature was recognized by the Swiss Electrical Industry with the ETA Prize for energy conscious applications of technology. Bypass Mains data screen This screen refers to the AC source supplying the bypass. Page 74 For parallel systems perform the following procedure on each unit, starting from unit no. Open the front door and make sure that: Follow this procedure only in case the UPS system and the load must be completely powered-down.
The rectifier, powered by the mains, supplies the inverter and the battery-charger keeps the battery fully charged. Before doing the following operations, make sure that you have shut down all equipment, which is normally powered by the UPS.